Empowering Customer Success through Operational Transparency
CyrusOne: Leveraging SynapSense to Improve Efficiency & Sustainability. CyrusOne is a data center provider, favorite of Fortune 1000 companies trading on the NASDAQ. Our objective was to improve SLA Management, save energy, recover cooling capacity. We deployed 768 EZ temperature sensors, 57 EZ humidity sensors, 26 Dual node ACU temperature sensors, 83 subfloor differential pressure sensors taking more than 513,600+ measurements per day. Replacing and relocating perforated tiles increased subfloor pressure, making it possible to achieve a more uniform underfloor pressure in the recommended DP range of 0.03 -0.045 in H2O. By strategically moving floor tiles to address over and undercooled racks, we were able to optimize the delivery of cooling to meet customer SLAs.